|Interbus Slave Cu - LonWorks|
The Anybus X-gateway copies I/O-data in both directions thus enabling data exchange between the two networks. Default I/O configuration is 20 bytes Input and 20 bytes Output. Changing default settings is very easy using the windows based configuration software Anybus Configuration Manager X-gateway from HMS (free of charge).
The Interbus 2Mbit/s interface module is a slave node that can be read from/written to by an Interbus master. Interbus has two ways of exchanging data; one through fast cyclical I/O data called ?Process Data?, and one through a somewhat slower protocol called PCP, which is mainly used for configuration purposes. It supports Interbus PCP V2.0. The module supports up to 10 words of data on the bus, out of which up to four words can be used for PCP.
The LonWorks interface is a high performance interface to LonWorks networks. The interface supports LonMark objects handling. The required network variables on the LonWorks side can be configured and stored in FLASH. It is based on MIP that allows high throughput and a configurable set of up to 256 input and 256 output network variables. The interface can, via the "LWtool" PC-based configuration utility program, link, and convert data between the other network side and devices located on a LonWorks Network. The LonWorks side of the product can be configured for any type of network variable e.g. SNVT's or UNVT?s.
|Individually isolated Bus In and Bus Out Interbus interfaces|
|Up to 10 words of Process data on Interbus|
|Interbus PCP v2.0 (0, 1, 2 or 4 words)|
|Special LW Config Software Tool for Network variable Setup|
|Certification prepared for Lonmark application layer interoperability guidelines V3.2|
|LonWorks FT-X1 Transceiver|
|Taille:||114 mm x 44 mm x 127 mm|
|Power Supply:||24 VDC (±20%)|
|Consommation:||max 400 mA|
|I/O Input:||Default 20 bytes, max 512 bytes (max 20 bytes as I/O on Interbus, max 256 network variables on LonWorks)|
|I/O Output:||Default 20 bytes, max 512 bytes (max 20 bytes as I/O on Interbus, max 256 network variables on LonWorks)|
|Power supply connector:||2-pole 5.08 mm Phoenix pluggable screw connector|
|Interbus Baudrate:||500Kbit/s or 2Mbit/s|
|Interbus connectors:||D-sub 9-pin ? Bus In male, Bus Out female|
|LonWorks baudrate:||78 kbit/s|
|LonWorks Connector:||5-pole 5.08 mm Phoenix pluggable screw connector|
|LonWorks Config:||LW Tool ABX for LonWorks interface variable configuration (included).|